What is that assortment of components on the control board?
Charge Controller - Power Input
The most basic charge controller disconnects the array when the battery is fully charged and keeps the battery fully charged without damage. The charging regimen is different for each type of battery. For example a charge controller designed for lead acid batteries should not be used with AGM batteries.
Input current, Output current, Battery type, Battery voltage
Series controllers stop the flow of current by opening the circuit between the battery and the PV array.
Shunt controllers divert the PV array current from the battery to a resistive load.
Solid State controllers provide more power and longer life to batteries
Pulse Width Modulation -
Maximum Power Point Tracking (MPPT) are smart DC to DC converters that optimize the match between the solar array and the battery bank. While theoretical gains of 50% in solar module output are possible the typical wattage gain using an MPPT is 10 – 15% vs. a PWM controller.
A controller should be sized 30% higher than the short circuit current of the solar array.
A switch to disconnect one circuit from another, the safety disconnects is used to isolate power generation or storage equipment from conditions such as voltage spikes or surges, thus avoiding potential damage to equipment. This is also an electrical code issue as power will be attached from batteries on output and PV on input.
Installation of many wind turbines requires a stop switch to short circuit the output for servicing or to prevent overspeed conditions. A short circuit causes resistance acting like a brake to slow the wind generator rotation down enough to stop the blades by hand. A Stop Switch also provides over-current protection, is usually installed on the controller board but can be installed anywhere between the wind generator and the batteries
An Inverter converts direct current electricity (DC) to alternating current (AC), to operate appliances directly or to supply power to an electricity grid. Inverters have a continuous output rating and a surge capacity rating. The latter rating is to support the inflood power surge when starting compressors such as fridges, freezers and electric motors such as well pumps.
Input Voltage (usually from 12V to 48V), Output Watts [the combination of amperage TIMES voltage is Watts], Output Frequency (always 60Hz in North America),
Stand-alone inverters convert DC power stored in batteries to AC power as required.
Synchronous Inverters are used to convert the DC output to AC power to be connected to the utility grid.
Multifunction inverters perform both functions.
Square Wave inverters are the simplest and the least expensive type of inverter, but it produces the lowest quality of power.
Modified square wave output are an economical choice in power systems where waveform is not critical. Output is created in 4 steps per cycle. High efficiency and large surge capacity of these inverters makes them ideal for impedance loads (motor loads). Frequently incompatible with light dimmers, copiers and laser printers and variable speed tools to operate properly. The modified wave output may cause a buzz on audio and video equipment.
Sine Wave inverters produce utility-quality sine wave power form.
Inverters frequently do not have fusing on their DC input side and require a DC rated fuse or braker, usually 30% greater than the inverter rating. All inverters should have a breaker protecting protecting output.
You'll need a battery charger when nature isn't being co-operative or when you use more energy than is stored. Most quality inverters include a battery charger packaged within the inverter. The battery charger is powered either by grid power or by a backup generator. Some inverters have the built-in ability to signal the generator to start when battery storage is low or when more power than is available through the battery changer is called for. Charging batteries properly requires administering the right amount of current at the right voltage. See our Batteries page to learn more about charging and different types of batteries.
AC Distribution Panel
Also called the main panel, or breaker panel or load center and used to be called the fuse box before breakers became popular. Size (amperage rating) is determined by building code, Inverter and generator ouput and your personal requirements.
Telephone: toll free at 1-888-810-4709
Ontario,Muskoka and Georgian Bay
© Copyright 2019, STRATEnerGY Inc.™
All Rights Reserved
Caribbean and US